After a period of time to run the generator set to do regular inspection, long line unit every 6-8 hours should be checked, spare units in the shutdown after the re-check again, check the site can be the following aspects: Lubricant oil residue , Air filter obstruction indicator, coolant level, radiator and external ventilation, the engine belt group, fuel oil supply and so on. Each time the unit is running for 50 hours, it is necessary to discharge the water in the oil-water separator and check to start the battery electrolysis level. After 200-300 hours of operation, the new unit shall check the valve clearance and check the injector: 400 hours per generator unit After the need to check and adjust the drive belt, if necessary, to replace, check the cleaning radiator chip and the discharge of sludge in the fuel tank; every 600 hours or at least every 12 months, need to replace the oil and lubricants filter; The frequency of the oil change cycle varies depending on the quality of the lubricating oil and the sulfur content of the fuel and the consumption of the lubricating oil in the generator. For every 800 hours of operation, change the oil and water separator and the fuel filter to check the turbocharger Whether to leak, check the intake pipe for leaks, check and clean the fuel pipeline; every 1200 hours after the operation to adjust the valve clearance; every 2000 hours after the operation, replace the air filter and coolant, thoroughly clean the tank radiator chip and water ; Every 2400 hours after the operation, check the injector, thoroughly check the cleaning turbocharger, a comprehensive inspection of the engine equipment.
Generator Set Operation
- Nov 10, 2017 -